Flameproof Ex d ˙ increased safety Ex e ˙ for indoor & outdoor applications
Cable glands ktA type (code: KTA)
The sealing ring blocks the cable on the under armour diameter. The addition of the sealing ring on the outer sheath guarantees a complete protection of the cable armour. Cable glands EMC tested by triaxial method, according to IEC 62153-4-3, IEC 62153-4-4 standards. Metric cable glands are made according to EN 62444 standard. Maintenance and installation operations and product selection must be done in accordance with IEC EN 60079-14 and 17 standards.
Surface - Group II
Approvals / Certifications
ATEX Certificate: INERIS 16 ATEX 0045X
IECEx Certificate: IECEx INE 16.0054X
EAC: RU C-IT.A 45.B.00909
Type examination certificate: INERIS 17 ATEX 3000 (Ex nR IIC Gc)
Ex db IIC • Ex eb II (gas) • Ex tb IIIC (dusts)
EPL (Equipment protection level)
Zone 1-2: Gb, Gc gas
Zone 21-22: Db Dc combustible dusts
Ex db IIC • Ex eb II • Ex tb IIIC
ATEX: EN 60079-0:2012 • EN 60079-1:2014 • EN 60079-7:2015 •
EN 60079-31:2014 • EN 60529:1991
IEC Ex: IEC 60079-0:2011 • IEC 60079-1:2014 • IEC 60079-7:2015
Ambient temperatures in services: sealing washers materials
Silicone seals -60°C ÷ + 80°C (code: SI)
Armoured: Single armoured cable SWA, Alluminium wire armoured cable AWA,Alluminium strip armoured ASA. Single wire braided cable SWB, Steel tape armored cable STA, Pliable wire armoured cable PWA. Screened flexible wire braided cable CY-SY.
Brass (code: OT) • Nickel-plated brass (code: ON)
AISI316L Stainless steel (code: S6) • Aluminium (code: AL)
ISO 262 Metrical
ANSI B1.20.1 NPT
DIN 40430 Pg
EN 10226 Gk (only for ATEX)
Degree of protection
The degree of protection assured by the cable entries is IP66 according to IEC/EN 60529 standard. For cable entries with cylindrical thread the degree of protection IP66 is assured by using either a flat silicone MVQ gasket of a flat PTFE gasket or a SILICONE MVQ O-ring. For cable entries with conical thread the degree of protection IP66 is assured by applying to the threading of sealing LOCTITE 241.
Metric cable glands are made in accordance to EN 62444 Standard.